# UPSCABLE # Defines the type of cable connecting the UPS to your computer. # # Possible generic choices for are: # simple, smart, ether, usb # # Or a specific cable model number may be used: # 940-0119A, 940-0127A, 940-0128A, 940-0020B, # 940-0020C, 940-0023A, 940-0024B, 940-0024C, # 940-1524C, 940-0024G, 940-0095A, 940-0095B, # 940-0095C, M-04-02-2000 # #UPSCABLE smart <----- コメントアウト UPSCABLE 940-0020B <----- Add This line
You are using a SMART cable type, so I'm entering SMART test mode mode.type = APCSMART_UPS Setting up the port ... <---- ちょっと待っててね。 Hello, this is the apcupsd Cable Test program. This part of apctest is for testing Smart UPSes. Please select the function you want to perform.
1) Query the UPS for all known values <-- 1) のＵＰＳのクエリを実行 2) Perform a Battery Runtime Calibration 3) Abort Battery Calibration 4) Monitor Battery Calibration progress 5) Program EEPROM 6) Enter TTY mode communicating with UPS 7) Quit
Select function number: 1
I am going to run through the series of queries of the UPS that are used in initializing apcupsd.
Simulating UPSlinkCheck ... Wrote: Y Got: SM Attempting to use smart_poll() ... Sent: Y Got: SM Good -- smart_poll() works!.
Going to ask for valid commands... Protocol version is: 3 Alert characters are: !$%+?=#| Command characters are: ^A^N^Z+-789>@ABCDEFGKLMNOPQRSUVWXYZ'abcefgjklmnopqrsuxyz~^M
Now running through apcupsd get_UPS capabilities(). NA indicates that the feature is Not Available
UPS Status: 08 Line quality: FF Reason for last transfer to batteries: S Self-Test Status: NO Line Voltage: 100.7 Line Voltage Max: 100.7 Line Voltage Min: 099.4 Output Voltage: 100.7 Batt level percent: 099.0 Batt voltage: 55.05 UPS Load: 034.8 Line freq: 50.00 Runtime left: 0033 UPS Internal temp: 040.5 Dip switch settings: 00 Register 1: 00 Register 2: 00 Register 3: 00 Sensitivity: H Wakeup delay: 000 Sleep delay: 180 Low transfer voltage: 090 High transfer voltage: 110 Batt charge for return: 00 Alarm status: 0 Low battery shutdown level: 05 UPS Name: UPS_IDEN UPS Self test interval: 336 UPS manufacture date: 01/25/06 UPS serial number: QS0605110406 Date battery replaced: 01/25/06 Output voltage when on batteries: 100 Nominal battery voltage: 048 Percent humidity: NA Ambient temperature: NA Firmware revision: 92.15S.A Number of external batteries installed: 000 Number of bad batteries installed: NA UPS model as defined by UPS: OWA UPS EPROM capabilities string: uD43132135138129uM43229234239224uA43110112114108uI43253264271280lD43103100097106lM43177172168182lA43090092081085lI43196188208204e44200155090oI43230240220225oD13115oJ13100oM13208s441HMLLq44202050710p443020180300600k4410TLNr443000060180300E443336168ON OFF The EPROM string is 253 characters long! Hours since last self test: NA
That is all for now.
1) Query the UPS for all known values 2) Perform a Battery Runtime Calibration 3) Abort Battery Calibration 4) Monitor Battery Calibration progress 5) Program EEPROM 6) Enter TTY mode communicating with UPS 7) Quit